# Introduction to the Delta Wye Transformer Part 7

Introduction to the Delta Wye transformer connection – Part 7.

In this section, we're going to look at how these transformer phase shifts are actually defined. Throughout this series, I've been using this definition for this transformer connection. This is a formal way of defining it and this is an informal way of defining it. So we'll take a look at how to interpret these two things.

To really understanding the phase shift of the transformer connection, we really have to understand the phase shift for the Delta Wye transformer connection, we have to understand the quantities that we're actually defining. We'll take a few moments to go over this very quickly.

VAG is the voltage measure across line A and ground. VBG is the voltage measured across line B and ground. And VCG is the voltage measured across line C and ground. And that's on the High Voltage side of the Delta side of our transformer.

Similarly, we have voltages that are measured across each individual windings. We have the HV winding and we have the LV winding here.

So winding A on the HV side – V phase A measured the voltage across the polarity side of winding A and the non-polarity side of winding A.  V phase B voltage measures the voltage across the polarity side of winding B and the non-polarity side of winding B. Same thing for V phase C on winding C.

Similarly, we're measuring the voltage across polarity side of the LV winding a and the non-polarity side of the LV winding a.

Same thing with winding b and winding c.

Now line-to-line voltages are a little tricky. So on the Delta side or the HV side, the line to line voltage across line A and line B we've labeled that as VAB which is also equal to the voltage across winding A or V phase A.

Now if you're having a hard time understanding this, just click on this link where we talked about this in the previous tutorials.

Because our transformer is connected in Wye as you can see here – wye grounded.  So the line to line voltage across line B and line C – we've labled that as VBC which is also equal to voltage across winding B on the HV side. And lastly, the voltage across line C and line A – we've labeled that as VCA and that is equal to the voltage across winding C.

Now the line-to-line voltage on the LV side is a bit more trickeier. So the line-to-line voltage across line a and line b is equal to voltage phase a times the square root of 3 and then shifted by 30 degrees. Now if you're having a hard time understanding that, just click on this link here where we talked about it in the previous tutorials. Similarly the line-to-line voltage across line b and line c, we've labeled that as Vbc and the line-to=line voltage across line c and line a, we've labeled that as Vca.

Oka so now that we've talked about all of these quantities, let's introduce one more quantity. You see that our low voltage side is correct in Wye correct? The LV side is also grounded. So all the none-polarity side are connected like that and they are all grounded. Which means that we can also label this voltage – which is measured across winding a – as Vag because the voltage measurement is across the polarity side of winding a and to ground – so Vag. Similarly, we can take the voltage across winding b on the LV side and call it Vbg – and lastly, do the same thing here – Vcg.

Okay there is one more thing we need to note about the voltage across primary winding and the voltage across the secondary winding.

This will be covered in part 7b.

This module was brought to you by GeneralPAC.com. Making Power System Protection, Automation, and Controls intuitive.

#### Greetings from the GeneralPAC Team!

We make high-quality Power Systems Video Tutorials on complex topics that are free and open to everyone!  Thank you so much for supporting us through Patreon so can continue doing good and valuable work.

What is Patreon and why do we use it?

Patreon is a fantastic portal that allows our fans and community to make monthly contribution (like Netflix subscription) so we can continue creating high-quality power systems video tutorials. In return, you get access to incredible perks like voting on future topics, getting your questions answered, access to VIP Q/A webinars with the creators of GeneralPAC, and much more! We THANK YOU for supporting us

Why do we need your support?

An incredible amount of time and effort is needed to develop high-quality video tutorials. Each video (Part 1 for example) takes approximately 10 hours to complete which includes learning the concept ourselves, brainstorming creative ways to teach and explain the concepts, writing the script, audio recording, video recording, and editing. It's no wonder why Hundreds-of-Thousands of people have watched, liked, subscribed, and left positive comments on Youtube channel. Your support truly makes all the difference.