This video was brought to you by GeneralPAC.com, making power systems Intuitive, Open and Free for Everyone, Everywhere. Consider subscribing and supporting through patreon.com/GeneralPAC. This is a mechanism for you to support us financially so we can continue making high quality power system video tutorials. Our corporate sponsor for this topic is AllumiaX.com from Seattle, Washington. Contact them for industrial and commercial power system studies.

Introduction to the Delta Wye Transformer Connection Part 6b.
In this part, we're going to continue our discussion on the voltage phasor diagram for the Delta Transformer connection. And by the end of this part 6 tutorial. Not this one but the part 6 section, we'll have a greater understanding what this illustration means – how it's drawn and what it represents. We often find this illustration in transformer nameplates as well as engineering drawings. So we want to have a very strong understanding of this connection.

So in part 6a, we setup our voltage phasors and we defined V_AG, V_BG, and V_CG. We also said that there is a difference between between V_AG vs V_AB or V_A. And that is the key to undersanding voltage phasor for the delta connection.

So let's jump right into it.

V_AB which is the voltage across line A and line B on the delta side. Is equal to the Phase A voltage which is the voltage across winding A. That is also equal to V_AG minus V_BG. Which makes sense right? A_AG is here which is the voltage across line A and ground. And V_BG is here which is the voltage across line B to ground.

So the voltage across line A and line B is essentially equal to the voltage across line A and ground minus the voltage across line B to ground. Make sense right?

Okay so let's evaluate this equation. So I've set something up already. This should look very similar to the examples that we've been doing in the previous tutorial. The first thing that we're going to do is that we're going to define our phasor values.

I'm going to choose a value for V_AG of 2400V at 0 degrees. V_BG is again 2400V at 240 degrees. And V_CG is equal to 2400V at 120 degrees. Now if you haven't caught on already, this is a balanced set of 3 phase voltages. And if you're still confused, you can click on this link here where you can find a video on balanced power systems. Okay so I'm going to call this phasor V_AG – because that's how I defined it right? So V_AG is at 0 degrees and 0 degrees is my reference line. V_BG is this phasor here. And V_CG is this phasor here. And, if you're having a hard time understanding this setup, just click on this link and go to the balanced power system video tutorial.

So this right here, is an ABC phase rotation. Now we said in our equation, that the line-to-line voltage across line A and line B which is essentially the voltage across our phase A winding for the delta connection is equal to V_AG minus V_BG. So here is V_AG right here. We're going to perform the head-to-tail method and substract V_AG minus V_BG.

Okay so now that we have a visual representation, if we were to relate V_AG to V_AB what would we have to do? We'll we would have to shift V_AG by 30 degrees – in the counter clock wise direction. And then, we would have to multiply it or stretch it by the 1.73 or the square root of three so it lines up with V_AB.

So we take V_AG – now we have to shift V_AG by 30 degrees in the counter clock wise direction. And then we have to multiply it or stretch it by 1.73 so it overlaps V_AB. Which means that V_AB is equal to the square root of three times V_AG rotated by 30 degrees. So this equal there. You see that?

So why are we doing this? Let's step back and understand exactly what's going on here and why we're doing this. We want to understand the relationship between V_AG and V_AB. Because that's what's going to help us understand the voltage phasor diagram for the delta wye transformer connection.

Is that making sense? If it is, then comment on below. If it's not, then tell me how I can improve these videos. Now if you haven't already go ahead and click on the link on your bottom hand of your corner of your screen.

In the next part – part 6c – we'll go ahead and complete our phasor diagram and show the relationship between these voltages here vs. these voltages there.

This video was bought to you by generalpac.com. Making power system protection, automation, and controls intuitive.

#### Greetings from the GeneralPAC Team!

We make high-quality Power Systems Video Tutorials on complex topics that are free and open to everyone!  Thank you so much for supporting us through Patreon so we can continue doing good and valuable work.

What is Patreon and why do we use it?

Patreon is a fantastic portal that allows our fans and community to make monthly contribution (like Netflix subscription) so we can continue creating high-quality power systems video tutorials. In return, you get access to incredible perks like voting on future topics, getting your questions answered, access to VIP Q/A webinars with the creators of GeneralPAC, and much more! We THANK YOU for supporting us

Why do we need your support?

An incredible amount of time and effort is needed to develop high-quality video tutorials. Each video (Part 1 for example) takes approximately 10 hours to complete which includes learning the concept ourselves, brainstorming creative ways to teach and explain the concepts, writing the script, audio recording, video recording, and editing. It's no wonder why Hundreds-of-Thousands of people have watched, liked, subscribed, and left positive comments on Youtube channel. Your support truly makes all the difference.