This video was brought to you by GeneralPAC.com, making power systems Intuitive, Open and Free for Everyone, Everywhere. Consider subscribing and supporting through patreon.com/GeneralPAC. This is a mechanism for you to support us financially so we can continue making high quality power system video tutorials. Our corporate sponsor for this topic is AllumiaX.com from Seattle, Washington. Contact them for industrial and commercial power system studies.

In the previous part, we solved a practical example where we sized a capacitor for power factor correction. In this part, we will verify if the size which we selected is optimal or not. Additionally, we will consider the consequences of over sizing the capacitor as well.

In the previous part 4a, we used our engineering judgment to decide on a capacitor of size 70 microfarads for our power factor correction requirements. We will now verify whether our selection has any positive effect on the system.

Let’s revisit the example used in part 4a.

We will now insert a 70 microfarads capacitor into the system

Since we sized a capacitor of 70 microfarads, we will need to calculate the reactive power which it will supply to the system in order to improve the power factor. A 70 microfarad capacitor gives us a capacitive reactance of 45.473 ohms

Using the derivative of Ohm’s law, we can find the reactive power as follows:

Reactive power =
(480)2 / 45.473
= 5.066kVAR

So, a 70 microfarad capacitor will supply a reactive power of 5.066 kilo VARs. Recalling the operating mechanism of the capacitor, we can see that the phase angle of the reactive power supplied by the capacitor will be 180 degrees out of phase from the reactive power required by the inductive load. Therefore, it will directly oppose its effect.

Mathematically we can subtract both quantities to get the reactive power of the system.

Reactive power = 5.18 kVARs – 5.066 kVARs = 0.114 kVARs

Using this newly calculated value of reactive power, we can calculate the apparent power using the Pythagoras theorem, which comes out to be 5.0013 kVA.

Apparent power= √(real power)2 + (reactive power)2

The effect of the capacitor can be visualized by adding an opposing vector to the reactive power in the power triangle.

The new power factor comes out to be 0.99 which is close to ideal.

5kW / 5.0013kVA
= 0.99

This is one of the many ways we can use to bring our power factor close to unity. We can redraw the power triangle to visualize the effect.

The phase angle between the apparent and true power now comes out to be 8.1 degrees, which is massive reduction from the original phase angle of 46 degrees.

Cos-1(0.99) = 8.1o

But what if we used a capacitor of 72 microfarads instead of 70. If we redo the entire calculation for a 72 microfarads capacitor, then the resultant reactive power will come out to be more than what the inductive load requires. And the extra reactive power supplied by the capacitor will result in a leading power factor for the system, where the current will start leading the voltage by a phase angle.

A leading power factor can cause additional problems for the system such as an unnecessary rise in the system voltage. The negative phase angle would become dangerous for sensitive equipment and even possible damage to the generator, whose voltage regulator will not be able to handle the spontaneous changes in the system voltage and fail to adjust accordingly.

We will discuss generator protection in a future topic. With that given and said, we will now conclude the introduction to the power factor series.

We hope, you have a continued interest in this topic and series as a student or professional. We also hope you find this content useful and enlightening. Please consider subscribing to GeneralPAC.com or becoming a patron on patreon.com

GeneralPAC.com. Making Power Systems Intuitive and free to everyone, everywhere.

#### Greetings from the GeneralPAC Team!

We make high-quality Power Systems Video Tutorials on complex topics that are free and open to everyone!  Thank you so much for supporting us through Patreon so we can continue doing good and valuable work.

What is Patreon and why do we use it?

Patreon is a fantastic portal that allows our fans and community to make monthly contribution (like Netflix subscription) so we can continue creating high-quality power systems video tutorials. In return, you get access to incredible perks like voting on future topics, getting your questions answered, access to VIP Q/A webinars with the creators of GeneralPAC, and much more! We THANK YOU for supporting us

Why do we need your support?

An incredible amount of time and effort is needed to develop high-quality video tutorials. Each video (Part 1 for example) takes approximately 10 hours to complete which includes learning the concept ourselves, brainstorming creative ways to teach and explain the concepts, writing the script, audio recording, video recording, and editing. It's no wonder why Hundreds-of-Thousands of people have watched, liked, subscribed, and left positive comments on Youtube channel. Your support truly makes all the difference.